Below is a list of previously identified and resolved SolarAPP+ issues. If you have a question on any of the issues listed below, or to report a new issue, please contact [email protected].
For an up-to-date list of current issues & bugs, along with upcoming improvements, please visit SolarAPP+ Contractors Guide: Issues & upcoming improvements.
Not selecting to use a 20A breaker upsize for microinverters and calling a 15A instead.
Inspection Checklist auxiliary grounding electrode
Inspection checklist auxiliary grounding electrode is not required by the code. After evaluating the option to update the inspection checklist, it was determined that the supplemental electrode 250.53(A)(2) is different from Auxiliary Electrode (690.47), which is a required facility ground. Therefore, the issue was dismissed.
Fixed: June 2021